The “Application Grid Gateway” supports power distribution grid operators in assessing grid performance. This application allows grid operators to use their existing distribution grid more efficiently, while avoiding unnecessary grid expansion. The measurement technology required in the substation for both the transformer and low-voltage outputs can be easily retrofitted.
The measurement values of the medium voltage, transformer, low-voltage outputs, valve positions and temperatures are transmitted to the grid control system via IEC 60870-5-104. Commands and setpoints can also be received and processed. External measurement systems such as short-circuit/ground-fault direction indicators can be easily parametrized via Modbus RTU. The entire parameterization can be stored in a clear manner and, if necessary, added to other stations. The option of simulating measured data makes it possible to commission new substations at the station builder's location from the grid control system without the field side being connected.All data, for example the measured values from the low-voltage outputs, can be communicated via MQTT to a cloud.
Asset managers can more accurately plan substation maintenance cycles by accessing both stored data and digital drag indicators. In the event of maintenance or grid errors, remote access helps prepare grid managers for the on-site conditions.
Remote updates for software modules and extensions are possible, eliminating unnecessary in-the-field service.
Upon request, WAGO will provide you a hardware solution tailored to your customers' substations.Patch and device management is available for the administration of a large number of distributed telecontrol devices with the WAGO Application Grid Gateway. This enables application updates, configuration changes, security patches and firmware upgrades, among other things.
Number of LV outlets: up to 17 NS outletsFirmware: Hardening in compliance with BDEW White Paper
Patch/device management: Application updates, configuration changes, security patches and firmware upgrades
Communication to the grid control system: IEC 60870-5-104
Communication to the office network: HTTPS, MQTT
Memory requirement on the SD card: less than 2 MB measurement data per day for 15 LV outlets
Authentication: local, LDAP
User groups: network management, network installer, network planner, asset manager, administrator
Network interfaces: secure separation between SCADA and office network
750-8210; PFC200; G2; 4ETH
750-8210/025-000; PFC200; G2; 4ETH; T
750-8210/040-000; PFC200; G2; 4ETH; XTR
750-8211; PFC200; G2; 2ETH 2SFP
750-8211/040-000; PFC200; G2; 2ETH 2SFP; XTR
750-8212; PFC200; G2; 2ETH RS
750-8212/025-001; PFC200; G2; 2ETH RS; TELE; T
750-8212/025-002; PFC200; G2; 2ETH RS; TELE; T; ECO
750-8212/040-000; PFC200; G2; 2ETH RS; XTR
750-8212/040-001; PFC200; G2; 2ETH RS; Tele; XTR
750-8212/040-010; PFC200; G2; 2ETH M12; RS; XTR
750-8217; PFC200; G2; 2ETH RS; 4G
750-8217/025-000; PFC200; G2; 2ETH RS; 4G; T